This guide assumes that you have already purchased the Intesis plugin from within the automationbridge interface, and that you have setup the Intesis device on your WiFi network.
Please Note : This plugin will only support the Intesis ASCII / WMP based controllers, not the IntesisHome range at this time.
Step 1 - Add the plugin via the Network Devices/Plugins page
Step 2 - Enter a name of this unit, and its IP address, and then click Next.
Step 3 - The automationbridge will then try to connect to the controller, and if successful the following will be displayed, click Next to proceed.
Step 4 - The Fibaro VD/Quick apps will be created for you, and confirmed.
Click OK to finish the setup, you will then be taken to the plugin settings page, from here you can add/remove any additional Intesis controllers.
If you are running the Fibaro HCL/HC2 controller, you will find the following device has been added for control.
And also the following global variables, that can be used in scene logic, or as triggers.
MODE_XXXX : 0=OFF, 1=HEAT, 2=COOL, 3=AUTO, 4=DRY, 5=FAN
FAN_XXXX : AUTO, 1, 2, 3, 4
If you are running the Fibaro HC3 Controller, you will find that a native HVAC device has been added.
Please note: While the Fibaro device shows both Heating & Cooling setpoints, the Intesis unit does not have this facility, so setting either will have the same effect of setting the single setpoint on the A/C unit.
Returning to the home page of the automationbridge, you will now be able to set this up for all 3 of the voice platforms, and it will be then presented as a native HVAC/climate control device.